The International Fire Code
2015 Edition, as adopted by the state of Washington as Chapters 51-54A including Appendices B, C, and only Sections D101, D102, D103.5, D103.6, D105 , of Appendix D and Appendix J, is adopted by reference with the following amendments:
108.1 is amended to read as follows:
108.1 .In order to determine the suitability of alternate materials and type of construction and to provide for reasonable interpretationsof the provisions of this Code, the Board of Adjustment of the City of Anacortes is hereby empoweredto act as a Board of Appealsfor this code. The Fire Chief andthe Building Official shall be non-voting ex-official members of said Board of Appeals.
503. 6 is amended to read as follows .
503. 6. 1Security gates that hinder or prevent access to Fire Department or EMS agencies in any commercial occupancy, or property serving four (4) or more residential occupancies shall require an approved automatic opener activated by opticom and a secondary means to manually open the gate in the event of power failure.
Section 5704.2.14 is amended to read as follows
Section 5704.2.14.3 The removal of underground storage tanks must be performed by, or directly supervised, by an individual certified by the International Code Council as
andUnderground Storage Tank Decommissioner or other approved certification.
(Ord. 2992 § 1 (Att. A), 2016; Ord. 2981 § 1, 2016; Ord. 2905 § 2(App. A), 2013)